Project TagsArc Flash
Computational Fluid Dynamics
This large financial data center was fully designed and never built due to company mergers. The building consisted of two data room floors of almost 40,000 square feet each. The mechanical and electrical systems are designed to Tier 4 redundancy. Electrically, a tri-redundant system is supported by seven 2.5 MW generators with an ultimate build out of twelve. Mechanical cooling is provided by four 1,110 ton centrifugal chillers with an ultimate build out of six. Thermal storage tanks provide 200,000 gallons of water during an event with almost 115,000 gallons of condenser water storage for the dry desert conditions.